Distribution system reconfiguration has two main objectives, namely as optimization of network operations and as system recovery in case of disturbances. It is necessary to consider the reconfiguration process and the process of using Distributed Generation (DG) or microgrid as an additional supply to reduce the possibility of failure, loss of power, or a voltage drop. Therefore the first step in research This results in the candidate bus 14 and bus 52 on the Mulyosari feeder which must be reconfigured by cutting off the flow at L13 and L50 because the losses on both buses are the worst with a value of 0.01370MW and 0.00900MW using the calculation algorithm of Binary Particle Swarm Optimization (BPSO) to predict the location of possible failures and the placement DG, and selected on bus 29 and bus 45 which were injected DG with a PV capacity of 15 kW each, after the self-healing was applied to the system, power flow analysis was carried out, and get good results g is very satisfactory with the total losses in the system decreased from 0.363MW to 0.116MW from this study we can conclude that self-healing can only be done if the distribution system is a complex radial.
|Journal||Journal of Physics: Conference Series|
|Publication status||Published - 6 Dec 2021|
|Event||3rd International Conference on Advanced Engineering and Technology, ICATECH 2021 - Surabaya, Indonesia|
Duration: 2 Oct 2021 → …